Title: maintenance schedule for steam room boiler
Post by: Peanut on November 15, 2010, 07:52:01 AM
How often should we be deliming our boiler? How do you know when are there any tell tale signs to look for?
Title: Re: maintenance schedule for steam room boiler
Post by: Jennifer on June 02, 2011, 12:26:59 PM
Look to your boiler manufacturers Installation, Operation and Maintenance manual to review what they suggest be performed. Or give them a call.
Water conditions, hours of operation, etc. can effect cleaning frequency.
Generally, a commercial boiler needs to be blown down under pressure every night, twice if the club is 24/7. Approximately every 3 months, the elements should be pulled and the tank cleaned of all lime buildup. All orifices should be checked & cleaned and all electrical inspected.
Contact a SteamSaunaBath Technical Specialist for assistance at 800-707-2862
Report to moderator 184.108.40.206